Floating Roof Tank Fires are Common
There are some 15 to 20 known Floating Roof Tank (FRT) fires per year. Floating Roof Tanks are especially vulnerable to the direct and indirect effects of lightning. Direct, or a nearby lightning strike can cause electrical current to flow across the tank shell and roof. When these lightning currents arc across the roof/shell interface, they can ignite any flammable vapours present with devastating effect.
As an example, if the lightning strike hits an adjacent stack. This strike can cause the charge in the tank walls to discharge rapidly. The prolem of leaving a ‘bound charge’ suspended in the product itself. Hence, failing to earth or ground the tank robustly. Therefore this situation can create a secondary arc. Igniting the vapours!
This typical scenario highlights why lightning does NOT have to hit the tank itself to cause an explosion or fire.
Reducing the Risk
Floating Roof Tank SHUNTS shown in the image above, used for many years as the default method to earth-out (ground) the roof to the tank wall.
Studies by the API (American Petroleum Institute) have shown these shunts often fail to provide the required contact between the roof and wall. They are prone to wear issues as well as being sensitive to tank deformation. Without a properly earthed roof, the risk of FIRE is very high.
So, knowing shunts are not the complete answer for Floating Roof Tanks; especially for the larger tanks. Competent engineers will install secondary bypass conductors to close-out the risk of the shunts not performing to prevent arcing at the roof/shell interface. But it doesn’t stop there!
What else do you need to consider?
Lightning has a complex personality. It is made up of multiple frequencies from DC to Megahertz (MHz). Thus, the lightning current can, in turn, exhibit many behaviours or responses, unlike a single power frequency related fault. The average energy released in a single lightning flash to the ground is 55 kWh. A significant amount of energy by modern generation standards.
According to IEC 62305, Lightning current magnitudes for a Class I, lightning protection level (LPL) consider and design to withstand 200 kA. A feature of lightning currents is the fact that most of this energy expends in only 100 to 300 microseconds and that the lightning reaches peak current in a matter of microseconds, i.e. it manifests in the form of a ‘pulse’ (discharge).
What does this mean for the Floating Roof Tank?
Substantially reducing the risk of sustained arcs for the Floating Roof Tank requires a reliable, full-time, low impedance and low-resistance connection between the tank shell and roof. The low impedance is desirable due to the higher frequency components of a lightning strike. The low resistance is necessary to ‘mop-up’ the lower frequencies efficiently until the discharge process (current flow) has finished. All this, regardless of the tank shell’s condition and geometry.
One option is to rely on the tank shunts as the only protection measure. But as mentioned earlier, this carries a significant risk of failure when you most need it. Large tanks deform during high winds, i.e. in storms! Compromising how the shunts perform. Over time, the shunts themselves take on deformation and effectively get stuck into positions that are not in contact with the shell. For every shunt not in connection with the tank, shell equates to an increase of arcing and overloading the remaining shunts. No prizes for what can happen next!
Supplement the shunts with a conventional direct cable connection from the shell wall to the roof. Although not an elegant, it does add a layer of mitigation by providing a low resistance connection, at least. The downside is the risk of cable-snagging and getting cut without anyone noticing until it’s too late. Inspections of live tanks at high-level usually require special breathing equipment and pre-planning as part of scheduled maintenance. Therefore, seeing a severed cable may take many months.
Also, the cable is fixed length, therefore, fixed impedance regardless of roof position. This impedance can be quite high if not carefully considered. The low impedance bond is particularly important if the tank suffers a direct strike discharging the energy more locally, and at the higher frequency component of lightning plays a more significant role.
Option three adds another layer on from the previous options by connecting the wall-roof directly with a low-resistance-low-impedance conductor. In real-life, these retractable conductors are distributed around the tank perimeter shell at equidistant spacings to share the lightning current load evenly.
Bypass conductors compliant to API RP 545 are an incredibly simple way of achieving a robust electrically continuous path between the floating roof and tank wall 100% of the time. This continuos path keeps both the wall and roof at the same potential, without the risk of severing a cable or any shunts failing.
This option gives you the peace of mind that the contents of your tank will not ignite due to lightning-induced issues. Although it has to be noted that the correct installation of the Bypass conductors is critical, get this bit wrong, and any benefit from the retractable conductors evaporates – so it is advisable to get the units installed (preloaded) correctly from the outset by a competent ‘trained’ engineering team.
If you are at the point of reconsidering your existing shunt system Why not email us so we can discuss the next steps.